Supported device types and versions
Communication line configuration
Communication station configuration
I/O tag configuration
Changes and modifications
MODBUS RTU MASTER supports data reading from the analyzers Circutor CVMk.
There can be defined the following parameters:
|Key word||Full name||Meaning||Unit||Default value|
|RC||Retry Count||Number of retry calls when an error in communication occurs.||-||2|
|RT||Retry Timeout||Delay between retry calls if an error in communication occurs.||ms||200 millisec.|
|WFT||Wait First Timeout||First waiting on the response after sending a call.||ms||100 millisec.|
|WT||Wait Timeout||Delay between the readings of a response until it is completed.||ms||100 millisec.|
|MWR||Max Wait Retry||Number of retry response reading until it is completed.||-||15|
String with protocol parameters is written according to this rule:
If a key word with valid value has not been found in the initial string, default value is used according to Table 1.
I/O tags: Ai
Address – decimal number in the range of 0 to 65535 – number of MODBUS double register.
The values are read by 2 registers and interpreted as a 4 byte integer. The addresses of values are described in literature about Circutor.